When the air shower room is installed at the entrance of the clean room, there should be no gap between the air shower room and the wall panel of the clean room. If there is air leakage, please trim the edge with sealant, and pay attention to the level of equipment installation, otherwise the door opening and durability will be affected. The equipment is divided into base type and non base type. The base type can be adjusted directly and then filled with silica gel. The non base type needs to be fixed with expansion screws and then filled with silica gel.
1。 Many people wind shower regularly use the instrument to measure the technical indicators of the equipment. If it does not meet the requirements of technical parameters, it should be handled in time!
3。 When it is found that the wind speed changes, first check whether the surface of the primary air filter turns black. If it turns black, it means that the pre filter contains more dust and the resistance increases. In other words, the non-woven fabric in the primary air filter should be removed for cleaning or replacement.
6。 After the replacement of the high efficiency filter, it is necessary to confirm that there is no leakage in the frame, and the dust particle counter is used for detection, and the normal operation can be carried out after reaching the technical indicators?
4。 If the wind speed cannot be increased after replacing or cleaning the non-woven fabric, it means that the high-efficiency air filter has been blocked, resulting in increased resistance. It is necessary to remove the spray ball plate, take out the high-efficiency filter by one person and two people in the room, and replace the high-efficiency air filter according to the specifications and models of the original high-efficiency filter. During installation, the arrow mark on the high-efficiency filter should be confirmed, and the arrow should point to the direction of air flow. The air shower room shall be sealed well to prevent leakage.